LIHI Certificate #108 - Gilman Hydroelectric Project, New Hampshire
The boundary between Vermont and New Hampshire passes through the project so that the 2.25 MW generating unit and the 1.0 MW generating unit are located in New Hampshire, while the two 0.8 MW generating units are located in Vermont. The project dam is 324.5 feet wide spanning the width of the Connecticut River. In 1995 and 1996 the Simpson Paper Company, who owned and operated the site to produce paper until 1999, spent $4.7 million to refurbish the dam by replacing the existing timber crib dam structure with a concrete gravity structure and adding rubber dam crest controls to the new and existing spillways. The dam includes an overflow spillway section containing a hydraulically operated crest gate. The new concrete spillway dam has a crest elevation of 826.8 feet and repaired existing concrete dam sections have rubber dam crest controls to elevation 833.3 feet (fully inflated), the normal head pond elevation. The rubber dam body on the new dam section is 6.5 feet high and 109.5 feet long. The rubber dam body on the existing dam section is 5.0 feet high and 108.0 feet long.
The Project is operated as a run-of-river facility, with outflow equal to inflow on an instantaneous basis, maintaining normal head pond elevation of 833.3 feet whenever possible, according to the U.S. Geological Survey (USGS). The Project incorporates a 27-foot wide hydraulic crest gate, which is operated to maintain the level of the head pond at the top of the rubber dams. The minimum flow needed to operate the Project is 130 cubic-feet per second (cfs). The maximum hydraulic capacity of the Project is 2,850 cfs. When river flows exceed this amount, it is spilled at the dam. When river flows fall below 130 cfs, such flows will also be spilled at the dam. The average gross head at the Project is approximately 24 feet from a head pond at elevation 833.3 feet to tail water at elevation 809.0 feet.
The Project impoundment at normal pond condition extends approximately 209 miles upstream of the dam to a point just above the confluence of the Johns River, at normal pond condition; the maximum surface area of the impoundment is approximately 130 acres at an elevation of 833.3 feet (USGS). The gross storage capacity at normal pond condition is estimated to be approximately 705 acre-feet, with an average depth of approximately 5.4 feet. The Project powerhouse is located at the northern Vermont end of the dam on the right bank of the Connecticut River and was originally constructed as a ground wood mill. The powerhouse has a substructure of mass concrete with integral water intake draft tubes. The superstructure is of brick construction with steel-frame and timber-frame construction. Project controls and mechanical equipment are located inside the powerhouse.
There are four turbines at the Project; the turbine units are numbered 1 through 4, from south to north. Wheel No. 1 is a horizontal tube turbine installed in 1985 and 1986. Wheels Nos. 2, 3 and 4 are contained in turbine pits, each approximately 20 feet wide. Wheel No.2 is a vertical single-regulated propeller turbine with adjustable wicket gates. Wheels Nos. 3 and 4 are horizontal Francis turbines. The combined installed capacity of the Turbine Generators is 4.85 MW. Generators No. 2, 3 and 4 are direct connected to the turbines; Generator No.1 utilizes a speed increaser, allowing the generator to turn at 900 rpm while the turbine turns at 150 rpm. The Project is both manually and automatically operated. The water wheel and Generator No.1, installed in 1985 and 1986, are automatically controlled. The three other turbines and generators (Nos. 2, 3 and 4) are manually controlled.
|LIHI Certificate No.||108|
|LIHI Certificate Term||December 4, 2017 - December 3, 2022|
|Owner||Ampersand Gilman Hydro LP|
|State||Vermont, New Hampshire|
|Location||Located in the Village of Gilman, VT in the Town of Lunenburg, Essex County, Vermont, and in the Town of Dalton, Coos County, New Hampshire, at river mile 300 on the Connecticut River.|
|Installed Capacity||4.85 MW|
|Average Annual Generation||25,000 MWh|
|FERC No.||P-2392 issued 1994, expires 2024|
June 19, 2018 – The 30-day appeal window for the preliminary recertification decision of the Gilman Hydroelectric Project closed on June 14, 2018 with no appeals to the decision received. The decision is therefore final and the Gilman Hydroelectric Project is recertified for a 5-year term from December 4, 2017 through December 3, 2022.
May 15, 2018 - On May 14, 2018, the Gilman Hydroelectric project has received preliminary approval for a new 5-year term of Low Impact Certification, with the following conditions:
Condition Satisfied 2020. Condition 1: By December 31, 2018, the Owner shall provide LIHI with evidence of compliance with the water quality monitoring and with the other recommendations issued by NHDES in its letter dated April 13, 2018. When available, the Owner shall provide evidence of concurrence from NHDES that the Facility does not negatively impact water quality.
Condition 2: By July 31, 2018, the Owner shall submit the final Drawdown Management Plan to USFWS and LIHI. When available, the Owner shall provide evidence of concurrence by the agencies on the plan. In the annual compliance statements to LIHI, the Owner shall provide a summary of activities related to dwarf wedgemussel during the prior year including any takings, agency communication and consultation, issuance of an agency Biological Opinion, and/or changes in operations or facilities that may affect the species.
This decision is preliminary pending the 30-day appeal window. Only those who commented in the initial application 60-day comment period are eligible to file an appeal. Such appeal needs to include an explanation as to how the project does not meet the LIHI criteria. Appeal requests can be submitted by email to email@example.com with “Gilman Hydroelectric Project” in the subject line, or by mail addressed to the Low Impact Hydropower Institute, 329 Massachusetts Ave, Suite 2, Lexington, MA 02420. All requests will be posted to the website and the applicant will have an opportunity to respond and any response will also be posted. Requests must be received by 5 pm Eastern time on June 14, 2018. The full application and reviewers report are available at the bottom of this page.
If no appeal requests are received and the decision becomes final, the new term for the Rolfe Canal Project will be September 6, 2017 through September 5, 2022.
February 20, 2018: The Low Impact Hydropower Institute has received a complete application for a new term of Low Impact Certification for the Gilman Hydroelectric Project.
LIHI is seeking public comment on this application. Specifically, we are interested in knowing whether you think the Gilman Project meets the LIHI Low Impact Certification Criteria, as revised in the 2nd Edition Handbook. Please review the program and criteria in LIHI’s revised Handbook and then review the Project’s 2018 application materials posted below.
Comments that are directly tied to specific LIHI criteria (flows, water quality, fish passage, etc.) will be most helpful, but all comments will be considered. Comments may be submitted to the Institute by e-mail at firstname.lastname@example.org with “Gilman Comments” in the subject line, or by mail addressed to the Low Impact Hydropower Institute, 329 Massachusetts Avenue, Suite 2, Lexington, MA 02420. Comments must be received at the Institute on or before 5 pm Eastern time on April 21, 2018 to be considered. All comments will be posted to the web site and the applicant will have an opportunity to respond. Any response will also be posted.
October 12, 2017: The Gilman Hydroelectric Project certification term has been extended to March 31, 2018.
May 28, 2013: The Gilman Hydroelectric Project has been certified as low impact for a five year term, effective December 4, 2012 and expiring December 4, 2017.
February 4, 2013: The public comment period on application has closed.
December 4, 2012: Ampersand Gilman Hydro LP has submitted an application for the certification of its Gilman Hydroelectric Project. The application was posted to the website and the public comment period was opened.
- Gilman Hydro Appendix 1-1 FERC Order Appr Trnsfr of Lic(P-2392)
- Gilman Hydro Appendix 1-2 FERC Order Issue New Lic(P-2392)
- Gilman Hydro Appendix 3-1 Gilman Project Location Map
- Gilman Hydro Appendix 3-2 Map of Nearby Dams on the CT
- Gilman Hydro Appendix B-1 VT DEC Water Quality Certification w. Amendment
- Gilman Hydro Appendix B-2 Nh DES Water Quality Certification w. Amendment
- Gilman Hydro Appendix B-3 Minimum Flow Release Plan dtd Aug 11 1994
- Gilman Hydro Appendix B-4 FERC Ordr Approving Minimum Flow Release Plan dtd Aug 31 1994
- Gilman Hydro Appendix B-5 NHDES Modification of Water Qlty Sampling Rqmt dtd July 10 2002
- Gilman Hydro Appendix B-6 NHDES Water Quality Monitoring Report
- Gilman Hydro Appendix C-1 VT DEC Rqst for Downstream Passage dtd Feb 5 2007
- Gilman Hydro Appendix C-2(a)-(c) Complete Gilman hydro Dwn Strm Passage Correspondence 2007-2012
- Gilman Hydro Appendix C-3 Gilman Fish Passage Correspondence Timeline - Abbreviated
- Gilman Hydro Appendix C-4 VT DEC Grant of Extension Rqst dtd April 8 2012
- Gilman Hydro Appendix C-5 USFWS Response to Gilman Rqst for Extension
- Gilman Hydro Appendix C-6 May 2012 Gilman Dwn Strm Passage Rpt
- Gilman Hydro Appendix C-7 USFWS Approval of Dwn Strm Passage
- Gilman Hydro Appendix C-8 VT DEC Approval of Dwn Strm Passage
- Gilman Hydro Appendix E-1 NHNHB & VTANR T&E Review Rqst
- Gilman Hydro Appendix E-2 USFWS Gilman Project Impact Review
- Gilman Hydro Appendix F-1 NH DRED Project Review dtd July 8 1985
- Gilman Hydro Appendix F-2 NH Div Hist Rsrc Rqst for Project Review dtd March 8 2012
- Gilman Hydro Appendix F-3 Gilman Project Review NH Div Hist Rsrcs dtd April 3 2012
- Gilman Hydro Appendix F-4 Resp from VT Hist. Pres to Rqst for Project Review
- Gilman Hydro Appendix F-5 VT Division of Historic Preservation Gilman Project Review dtd May 7 2012
- Gilman Hydro Appendix F-6 Essex Cnty Register of Historic Places dtd June 5 2012
- Gilman Hydro Appendix G-1 Gilman Hydro Recreation Compliance Cert dtd May 15, 1995
- Gilman Hydro Appendix G-2 VT Dept. of Parks & Rec Cert of Gilman Recreational Compliance dtd 3.8.12
- Gilman LIHI Application
- Reviewer Report_Gilman_5.20.2013