LIHI Certificate #132 – Dog River Hydroelectric Project, Vermont
The Dog River Hydroelectric Project is located at river mile 11.8 on Dog River in Northfield, Vermont, in the Nantanna Mill complex, and powered by the Dog River and hydrology of the Green Mountains. In 1984, the Federal Energy Regulatory Commission (FERC) issued an exemption for this non conduit facility, P-6757.
There are three partially breached dams downstream and at least two partially breached dams upstream. This project operates in run-of-river mode. The project is required by FERC to provide 5 cfs continuous minimum flow; however, the project provides 20 cfs to the bypass section below the dam through a permanent notch in the flashboards, or maintaining 0.2′ of flow over the crest of the boards.
The hydro facility’s water intake sits beneath a protective screening of trash racks, flow then moves through a 7 ft diameter steel penstock with 25 ft of gross head before meeting 2 Kaplan turbines in the powerhouse. The water reunites with the Dog River about 130 ft downstream of the project’s reinforced concreate dam via an unlined, earthen channel. The Dog River Hydroelectric Project operates in a run-of-river manner, generating approximately 650,000 kilowatt-hours of clean, predictable energy each year. Gravity Renewables is dedicated to the preservation of Dog River Hydro and its contributions of renewable energy to the community.
|Project Name||Dog River|
|LIHI Certificate No.||132|
|LIHI Certificate Term||October 14, 2016 - October 14, 2021|
|Location||Dog River, river mile 11.8, Northfield, VT|
|Installed Capacity||222 kW|
|Average Annual Generation||650 MWh|
|Facility Type||Run of River|
|FERC No.||P-6757, exempt 1984|
March 30, 2017: On February 6, 2017, LIHI Executive Director Shannon Ames announced a Preliminary Certification Decision that the Dog River Hydroelectric Project (FERC No. P-6757) satisfies the LIHI Certification Criteria. The Dog River certification includes the following conditions:
Condition 1. During the term of LIHI certification, a minimum flow of 20 cfs, or inflow if less, shall be maintained in the bypass reach at all times, as such flows formed the basis of VT DEC’s position that healthy flows for fish, wildlife and water quality are being released. Deviations from this flow requirement shall be reported to VT DEC and summarized annually in the annual compliance letter to LIHI. If deviations occur, the owner shall explain the causes, the frequency and magnitude of them, the resulting environmental effects, and plans to avoid these deviations in the future.
Condition 2. By no later than October 31, 2017, the Owner shall supply operating records related to downstream flows from October 1, 2016, to September 30, 2017, to the Vermont Agency of Natural Resources, Department of Environmental Conservation (VT DEC). The parties shall evaluate operations to ensure run-of river operations are reliably maintained. By December 31, 2017, the Owner shall report to LIHI on the findings made by VT DEC relative to this data, along with any facility changes that may be found necessary to ensure continuing compliance.
As provided for in Section 4.2.5 of the LIHI 2nd Edition Handbook, notice of the preliminary decision to certify was posted on the Institute’s website and sent to the stakeholder email distribution list on February 7, 2017. A 30-day period was provided to anyone who commented on the original application to request an appeal, and no requests for appeal were received.
The Dog River Project is now deemed certified by LIHI for a five (5) year term. The effective certification date for the Dog River Project is October 14, 2016, expiring on October 14, 2021.
February 6, 2017: On February 3, 2017 LIHI issued a Preliminary Certification Decision that the Dog River Hydroelectric Project (FERC No. P-6757) satisfies the LIHI Certification Criteria.
As provided for in Section 4.2.5 of the LIHI 2nd Edition Handbook, the Preliminary Certification Decision, along with the Application Reviewer’s report and (if prepared) report of the Executive Director, will be posted on the Institute’s Web page for 30 days. Notice of the posting will be provided to all individuals or organizations that commented on the initial Application Package.
Any Commenter may submit a letter to the Executive Director requesting an appeal within the 30-day period which begins on February 7, 2017 and ends on March 7, 2017. The appeal request must state specific reasons why the hydropower facility should have failed one or more criteria. Only individuals or organizations that commented on the initial Application Package may file an appeal.
If no appeal is requested within the 30-day period, the Executive Director will issue LIHI Certification for the facility and post a notification of certification on the Institute’s website. Once final, the effective certification date for the Dog River Project is October 14, 2016 for a five (5) year term, which will expire on October 14, 2021.
January 6, 2017: LIHI has received a comment letter from the Vermont Department of Environmental Conservation in regards to the Dog River application for LIHI certification. The letter can be found in the Files section below.
January 3, 2017: LIHI has received a comment letter from the MadDog Chapter of Vermont Trout Unlimmited (MDTU) in regards to the Dog River application for LIHI certification. The letter can be found in the Files section below.
November 7, 2016: On October 14, 2016, the Low Impact Hydropower Institute (LIHI) received a complete application from Stuwe and Davenport Partnership Partnership, LLC, a wholly-owned subsidiary of Gravity Renewables, Inc. (Gravity), for the Low Impact Certification of the Dog River hydroelectric project, located in Northfield, VT (FERC P-6757).
LIHI is seeking public comment on this application. Specifically, we are interested in knowing whether you think the Dog River project meets the LIHI Low Impact Certification Criteria. The Dog River application is subject to review using the Criteria in the LIHI Certification Handbook of 2014. Please review the program and criteria in LIHI’s 2014 Handbook and then review the Project’s 2016 application materials posted on the project page. Comments that are directly tied to specific LIHI criteria (flows, water quality, fish passage, etc.) will be most helpful, but all comments will be considered. Comments may be submitted to the Institute by e-mail at firstname.lastname@example.org with “Dog River Project Comments” in the subject line, or by mail addressed to the Low Impact Hydropower Institute, PO Box 194, Harrington Park, New Jersey 07640. The 60 day public comment period begins on November 7, 2016. Comments must be received at the Institute on or before 5 pm Eastern time on January 6, 2017 to be considered. All comments will be posted to the web site and the applicant will have an opportunity to respond. Any response will also be posted.
The Dog River comment period has been extended to January 8, 2017.
- Dog River Project Certification Reviewer’s Report – January 2017
- VT Dept of Env. Conservation_Dog River LIHI Comments_01062017
- MadDog Trout Unlimited Comments to LIHI_re Dog River_01032017
- Dog River Application- 2016
- Tab 7 – Correspondence from Vermont DEC and USFWS
- FERC Exemption and Agreement
- 401 Water Quality Certification
- Dog River Wild Trout Evaluation